The One Stage Setpoint Control 150 is designed to operate a single component of a heating or cooling system in order to maintain a set temperature. It can be used in applications ranging from heating a swimming pool to maintaining a constant slab temperature in a commercial car wash bay. This control regulates a constant setpoint water temperature for heating or cooling. The 150 is designed to operate a single relay (rated at 240 V, 8 A) to control a single device such as a boiler, pump, or valve.
Heat or Cool Setpoint Control
Normally open AND normally closed relay
Pulse Width Modulation Control
|Control||Microprocessor control. This is not a safety (limit) control|
|Packaged weight||1.0 lb. (450 g)|
|Dimensions||4-3/4" H x 2-7/8" W x 7/8" D (120 x 74 x 22 mm)|
|Enclosure||White PVC plastic, NEMA type 1|
|Approvals||CSA C US, meets class B: ICES & FCC Part 15|
|Ambient conditions||Indoor use only, -20 to 120°F (-30 to 50°C), RH ≤90% Non-condensing|
|Power supply||24 V (ac) ±10%, 50/60 Hz, 1.3 VA, 24 V (dc) ±10%, 0.02 A|
|Relay||240 V (ac) 8 A max, 1/4 hp|
|Sensors||NTC thermistor, 10 kΩ @ 77°F (25°C ±0.2°C) ß=3892|
|-Included||Universal Sensor 071|
|-Optional||tekmar type #: 071, 078, 082|
|Warranty||Limited 3 Year Warranty|
In most cases the current version of literature will work, otherwise use the piece of literature most closely matching the date code of your product.
Jan 2011 - Present
Installation & Operation Manual
Dec 2008 - Present
Dec 2008 - Current
More advanced application drawings can be found in our Solutions section.