The Two Stage Setpoint Control 152 is a microprocessor-based control that operates as either a two stage setpoint control or as two independent setpoint controls. As a two stage setpoint control, the 152 can provide two stage heating, two stage cooling or a combined heating / cooling interlock function. When operating as two independent setpoint controls, the 152 can control any combination of heating or cooling device.
2 Stage operation or heat & cool control
Control of up to 2 different setpoints (with additional sensor)
Pulse Width Modulation
|Control||Microprocessor control. This is not a safety (limit) control|
|Packaged weight||1 lb (450g)|
|Dimensions||4-3/4" x 2-7/8" x 7/8" (120 x 74 x 22 mm)|
|Enclosure||White PVC plastic, NEMA type 1|
|Approvals||CSA C US, meets class B: ICES & FCC Part 15|
|Ambient conditions||Indoor use only, -20 to 120°F (-30 to 50°C), RH ≤90% Non-condensing|
|Power Supply||24 V (ac) ±10%, 50/60 Hz, 3 VA, 24 V (dc) ±10%, 0.03 A|
|Relays||240 V (ac) 10 A, 1/3 hp|
|Sensors||NTC thermistor, 10 kΩ @ 77°F (25°C ±0.2°C) ß=3892|
|-Included||Universal Sensor 071|
|-Optional||tekmar type #: 071, 078, 082|
|Warranty||Limited 3 Year Warranty|
In most cases the current version of literature will work, otherwise use the piece of literature most closely matching the date code of your product.
Jan 2011 - Present
Installation & Operation Manual
Dec 2008 - Present
Dec 2008 - Current
More advanced application drawings can be found in our Solutions section.